Default welcome msg!
Permeate flow rate:800 GPD (3.0 m3/day) Stabilized salt rejection: 99.2% Effective membrane area: 27 ft2 (2.5 m2)
1.The stated product performance is based on data taken after 30 minutes of operation at the following test conditions: • 500 mg/L NaCl solution at 100 psig (0.5 MPa) applied pressure • 15% recovery • 77 oF (25 oC) • pH 6.5–7.0
2. Minimum salt rejection is 99.0%.
3.Permeate flow rate for each element may vary but will be no more than 15%.
4.All elements are vacuum sealed in a polyethylene bag containing 1.0% SBS (sodium bisulfite) solution and individually packaged in a cardboard box.
Membrane type:Thin-Film Composite
Membrane material:Polyamide (PA)
Element configuration:Spiral-Wound, FRP Wrapping
FOR MORE INFORMATION SEE THIS
|Name||RE 2540-BLF Ultra-low pressure RO membrane element low TDS water 800 GPD CSM|